FIRE SQUAD BC TYPE FIRE EXTINGUISHER 6 KG Gas Cartiridge
Click Image for Gallery
FIRE SQUAD BC TYPE FIRE EXTINGUISHER 6 KG Gas Cartiridge• Sodium Bicarbonate based dry chemical powder
• Capable of fighting Class B and C fires.
• High quality Epoxy Powder Coating.
• CO2 Gas Cartridge Expellant .
• ISI Marked Hose Pipe
• ISI Marked Powder
• Brass nickel plated cartridge type heavy valve with squeeze grip operation.
• Rechargeable and easy to service.
Petroleum, Diesel, Flammable and volatile liquids
For Petrol pumps, Gas Filling Stations, Oil refining Industries etc.
*Note: Not recommended for use on expensive and delicate equipment like computers, etc.
Not Recommended for A, D and K Fires
|Ratings and Approvals|
|Confirming IS code||15683|
|Operating temprature range (C)||-10deg to +55 deg|
|Approvals :||ISI , IS 15683, CE|
|Capacity :||6 kg|
|Anti corrosive inhabitor||Exposy polyster powder coating|
|Type of extinguisher||Co2 gas cartridge|
|Type of extinguisher media||Dry powder IS 4308|
|Expellant||120gm gas cartridge|
|Minimum effective discharge (%)||85|
|minimum jet length||More than 2 mtr.|
|Discharge time (sec)||More than 13 sec.|
|Hydraulic test Pressure (kgf/cm2)||35|
|Charged Pressure (kgf/cm2)||16|
|Operating Valve||Squeeze Grip valve with Safety Seal|
|Class of fire where it CAN be used|
|Class B fire||Petroleum, oil Diesel, paint, varnish, solvent, avaition fuel, flammable and volatile liquids etc.|
|Class C fire/ Electrically Started fire||Flammable gasses, live electrical equipments, industrial gases, electrical installtion, power grid etc.|
|Class of fire where it CANNOT be used|
|Class A fire :||Wood, textile, paper, plastic, cloths, cotton mill, jute mill, small kitchen fire etc.|
|Class D fire :||in scientist laboratories or industries involving fire of magnesium, sodium, zirconium, aluminium etc.|
|Class K/F fire :||Commercial kicthens, edible oil and fat fires|
|Other instruction :||Fire Extinguishers are for small fires and for First aid Only|